Ellenton, FL residents rely on AC Today for exceptional air conditioning and indoor air quality services. From repair and maintenance to complete system replacements, we are your AC experts!
Read our reviews and find out why your neighbors consider us to be their nearby air conditioning company in Ellenton, FL.
for Ellenton, FL
Our Reviews by City
Great service. Love the maintenance contract
REGINA - Ellenton, FL
Marcus was knowledgeable and friendly. Answered all of my questions clearly and patiently. I asked for some quotes and he provided those for me before he even left the premises.
WILLIAM - Ellenton, FL
I had Quinton come out to my place and perform a pre season inspection / tune up on my HVAC system. Very pleased with ALL that he did for us.
Response from AC Today Heating & Air Conditioning:
Thank you William for the kind review. Quinton is one of the best! Our pleasure.
Efficient, Excellent service
BILL - Ellenton, FL
Eric was very personable, polite and respectful. He explained the service he did and answered all of my questions in detail.
HVAC MAINTENANCE DONE COMPLETE MAINTENANCE ON SYSTEM WASHED THE COILS DOWN AND DRAIN PAN AND DRAIN LINE OUT. UNIT IS RUNNING GOOD AT THIS TIME.
Returned and installed the 45/5 capacitor. Ac package unit is cooling properly.
Air conditioning service performed found System very very low on refrigerant and turning off due to low pressure sensor. Recommended replacement versus repair due to the age of the equipment customer needs to move some things around before she will have the money to purchase the unit. Quoted customer for new system she will call us next week
Performed a comp AC maintenance. All major components are operating properly. The run capacitor is very low. I will recommend and a maintenance plan.
HVAC MAINTENANCE DONE COMPLETE MAINTENANCE ON SYSTEM WASHED THE COILS DOWN AND FLUSHED THE DRAIN PAN AND DRAIN LINE OUT UNIT IS RUNNING GOOD AT THIS TIME.
Ac service call. Found the drain line backed up and not configured properly. Cleared the drain line . Gave estimate to install a condensation pump and re-insulate the air handler.
HVAC MAINTENANCE DONE UNIT NEEDS A UV LIHGT ON IT YOU CAN SEE GROWTH AND SMELL IT.
Returned to reinstall hurricane strap
Ac maintenance during maintenance found bad disconnect. Replaced disconnect system is now operational
Found loose wire. Re wired system is now heating
Please have ray work quote for replacement system vs replace compressor
HVAC MAINTENANCE DONE UNIT IS RUNNING GOOD AT THIS TIME WASHED THE COIL DOWN AND FLUSHED THE DRAIN PAN AND DRAIN LINE OUT.
Checked refrigerant pressure and secured refrigerant valve caps.
Complete maintenance on York package unit. Ac system working great in heat and cool modes. All amps pressures are in range. Changed 5” air filter for customer.
Performed an AC maintenance on a New York package unit. All major components are operating at manufacturers specs.
A/C REPAIR JUST REPLACED A TXV VALVE AND A EVAPORATOR COIL ON A TRANE PACKAGE UNIT. PUMPED SYSTEM DOWN TO 393 microns and recharged system to factory specs 7.5# R410
Performed a gold maintenance 2 of 2 . Older AC package unit system. Can’t read name plate. Found a small sticker with model number but the serial number isn’t visible. This customer is a part changer and won’t replace system unless compressor dies. Has a serious growth issue. He stated he has a ac guy on the side. Not sure why he uses us . Maybe to get a price and then calls the other guy to get a better price. FYI...
Finally got the customer approved for a 1 ton mini split with new copper line set and new high volt wire and line set cover. The customer is available Friday for the install. Customer want a call to verify Friday and what time the installers will be there.